4-35. LEFT AND RIGHT HANDGRIP (LONGBOW) ASSEMBLIES 2A4 AND 2A5 REPAIR (cont)
Components inside the RHG contain
electrostatic discharge sensitive (ESDS)
devices. Refer to paragraph 2-8 for handling
requirements before starting this task to
h. Install new springs (5) and caps (6).
Continuous pressure on handgrip against
housing assembly is required to keep
tension springs seated in handgrip
Ensure index plate is alined with pins on
i. Install new index plate (1) using four screws
j. Install LHG or RHG CCA (steps 1 through 6
k. Install LHG or RHG switches (steps 1
through 6 above).
END OF TASK